- checked home ECC ovens found that the gas doesn't come on after the oven has been running for an hour<br />
- supplied and fitted new rainhead at physics, cut old downpipes to suit<br />
- check AC in science foyer not turning off, went on roof and reset AC<br />
- ELC supply and fit new pit lid, core drill 100mm stormwater drain through, install new pit connecting to existing pit, excavate for water line<br />
- Admin fire hydrant, locate fire main in street, attempt to turn, needs to be cut and soldered <br />
- Pool air handler supply and install new filters, tension fan belt<br />
- ELC finnish off new pit connecting to main storm drain<br />
- ELC run new water line, excavate trench, drill through rock and supply and install new pit with float valve for new water feature in playground<br />
- pump truck to pump out grease traps on home ecc, canteen and science interceptor tank, clean interceptor tank pebbles<br />
- Check water stain on wall on CM Wood downstairs<br />
- cut off, spin around and resolder front gates fire booster point<br />
- Science heater didnt turn on, found schedule needed to be adjusted<br />
- Middle school heater re-adjust temperature set point<br />
- supply and fit second CM Wood fan<br />
- Check middle school staff heater not coming on, reprogrammed master controller<br />
- Supply and install new pan collar to kennedy cottage upstairs toilet<br />
- screw back flashing and re apply silicone to workshop leaking window<br />
- measure up uniform shop downpipe<br />
- inspect two big holes in gym roof, found seven dektites had perished<br />
- supply and install two new dektites on gym roof<br />
- check senior staff female toilets extraction, found has been turned off due to duct being cut, turned back on and retaped duct<br />
- supply and install new science downpipe<br />
- supply and install new mixer with vegetable spray in canteen<br />
- science blocked toilet<br />
- order new lever taps for arts<br />
- remove toilet and replace pan collar with new 20mm offset pan collar<br />
- fit new downpipe to science courtyard<br />
- supply and fit 2x new gas regulators to ovens in home ECC, recommission ovens.<br />
Check thermostat