Install tundish for new coolroom<br />
Check burst tpr valve on hot water in kitchen behind gym, order new tpr valve<br />
Supply and install new float valve to senior college girls downstairs toilet fifth from the left<br />
Scheduled middle school ACS for 2020<br />
Attend site after hours to look at tap that won't stop running in canteen, Replace washer on pot filler in canteen<br />
Check mixer in IJ day it has come loose Fan in pool pump room has a broken belt Fan dimensions 300 diameter by 355 lengths, three phase power available Room dimensions 5 x 8 X 2.2 <br />
Replace southwood boys fire hydrant washer Tighten IJ day mixer<br />
Weights room AC<br />
Supply and replace 2x buttons on urinals in southwood boys<br />
Paint all fire sluice valves lids<br />
Paint all water supply valve lids"<br />
Read light 2 ovens in home ECC<br />
Complete essential services, check all rangehoods in homework and commercial kitchen remove debris from fan on roof sign off in book sign of online.<br />
Check dishwashers in both commercial and domestic kitchens not draining,<br />
Tested all sinks found to be draining correctly,<br />
Checked dishwashers both with full of water, turned on dishwasher pressed pump button and both dishwashers pump the wastewater away correctly<br />
Check water on floor in gym staff toilets<br />
Ran basins in a joining room to see if water is coming from there<br />
Need to check roof cavity water pipes in walls<br />
Remove toilet pan, removed faulty pan collar and replace with new<br />
Reinstall toilet, pan test and commission<br />
Replace flexi connector to pillar tap which had burst,<br />
Order four new push button taps to replace faulty pillars<br />
Plunge and unblock toilet<br />
Inspect AC dripping water sound needs a new pump<br />
Check AC now blowing cold air<br />
Climb on roof and reset unit<br />
Blocked toilet<br />
Supply and install new bucket pump to AC<br />
Run new 13 mmm drain<br />
Run new 13 mm drain to other AC<br />
Test and comission AC pump<br />
Test and comission Panasonic AC after electrician replaced isolator<br />
Inspect AC dripping water, ordered a new pump<br />
Supply and install new cistern on toilet<br />
Inspect 2x air cons in server room<br />
Panasonic aircon not working at all<br />
Hitachi aircon working but icing up and pump dripping water on floor<br />
Found Panasonic outdoor unit on roof the isolator was full of water<br />
Ordered new pump for Hitachi unit will fit<br />
Supply and replace TPR valve in under bench HWS<br />
