Check roof leaks ELC windows<br />
Decommission uniform shop AC<br />
-remove and relocate around corner on wall bracket<br />
-extend copper<br />
Walk through school check for roof leaks after weekend<br />
Check IT server AC leaking<br />
-It server AC, thermal image and found only the top of the coil is getting cold<br />
Jet truck <br />
- Jet and vac storm water drains from pavillion gates up to CMW building<br />
Supply and install new rain head and relocate leaf eater rain head to a reachable level<br />
Heater servicing<br />
-Arts Building<br />
-Senior college<br />
-Woodworking<br />
-Home ecc<br />
-Double storey building<br />
-Cottage heater<br />
Science server AC inspect why unit keeps turning off, found low on gas<br />
Check arts sump leak, paint arts gutter sump with liquid flash<br />
Paint senior ventilation leaks with liquid flash<br />
Re-gas science AC<br />
-Reclaim old gas<br />
-cut off flare nuts, re flare<br />
-Nitrogen pressure test<br />
Weigh in correct amount of gas<br />
Unblock ELC kitchen drain with plunger<br />
Home ECC roof leak<br />
-found old lead flashing had come away, re attached and liquid flashed<br />
Cmw weather roof sheet<br />
Thermostatic valve testing<br />
-service all thermostatic mixing valves<br />
-test vales and failsafe<br />
Statcom ventilation inspection<br />
Ceramic room heater, turn off timer<br />
jnr lib computer room ac heater, climb on roof and reset<br />
CMW big gas heater, needs fan<br />
ELC blocked sewer, pipe hunter to jet clean<br />
Dig up io to remove wooden block from sewer<br />
Supply and fit new filter to gym/pool rinnai HWS<br />
Remove basin from boarding house and cap piping, too close to switch board<br />
Quote AC for Colebrook Hall<br />
Inspect new AC location with Al and Graham<br />
Cmw roof leaks, <br />
-remove old silicone and apply liquid flashing<br />
relocate clip up to perlin, attach clip to perlin, silicone up old hole<br />
