- check pool showers not getting any hot water, clean filters on hot water system <br />
- connect gas line to heater in year 9 <br />
- disconnect gas line and cap, relight all gas appliances<br />
- measure up and order new toilet suite<br />
- inspect water leak in IJ Day switchboard, looks like water is coming from electrical conduit.<br />
- locate and measure all pits on site ready for confined space audit.<br />
- supply and install new toilet in arts staff toilet<br />
- finish inspecting pits<br />
- check roof leak in IJ Day switchboard<br />
- check pool showers not getting any hot water, clean filters on hot water system<br />
- connect gas line to heater in year 9 <br />
- disconnect gas line and cap, relight all gas appliances<br />
- Supply and install new network controller on ducted heating system in Kennedy cottage<br />
- check CM wood roof leaks found water still getting in in one location went on roof found there was a screw missing rubber and a hole in the roof so sealed both up<br />
- check cm wood foyer roof leak down sheets at the end of the of the roof with folded up so screwed them down will check again next rainy day<br />
- check roof leak in ELC found new roof leak in room double zero 1/3 skylight down around a window sill will check when roof is dry enough to get on<br />
- blocked toilets in middle school girls downstairs unblocked with plunger<br />
- slow flushing toilet in colebrook girls poured momar down and slowly flushed away and then plunged will check again later<br />
- ELC roof leak, inspect roof leak in skylight found hole in old silicone, cleaned off old silicone and reapplied new silicon.<br />
- reprogrammed southwood boys HVAC system to come on at 4am and off at 3 pm<br />
- inspect home ec ovens and order new parts<br />
- admin AC not working, tried new remote, AC unit faulty<br />
- ELC solar hot water recirculating pump not working<br />
- check heater v001 pilot was lit but power was turned off turned unit on and tested OK<br />
- check AC heating boardroom second time looking at it for same problem have ordered new temperature sensor<br />
- check heaters in woodwork reported not working turned on and tested ok cleaned filters<br />
- check fire reel behind southwood boys, needs new valve<br />
- Home ec ovens<br />
- supply and install new fans to 2x ovens, supply and install 4x ignition leads, supply and install 2, fix cables that ran across the top of the fans<br />
- fit last thermostat to home ec ovens<br />
- check gas hot plates in home ec with Shelley and Margaret, hot plates are working.<br />
- heater in gym office reported not working, replaced filter and found a damper was closed so re-opened damper and secured in the open position<br />
- check roof leak above canteen, found old heater flue needs removing and hole patch<br />
- check tap in girls toilets in gym, found spindle has seized and will not turn and tap is dripping, ordered me tap sets<br />
- check heater in drying room at farm, found gas bottles were empty and have ordered any bottles to swap over<br />
<br />
<br />
Sent 8/8/2019<br />
<br />
