- ELC supply and install new concrete gatic lid to stormwater pit<br />
- ELC pit lids, drill in nut rivets and secure down pit lids with Allen key bolts.<br />
- Commercial kitchen ovens, supply and replace pilot blocks, injectors, thermocouples and ignition leads.<br />
- Remove old ducting from cm wood staff lunchroom<br />
- Finished ovens<br />
- replaced skylights over arts <br />
- reinstalled hot water dispenser in cm wood kitchen supplied and installed new flick mixer in cm wood kitchen<br />
- thermostatic mixer valve testing <br />
- gym kitchen fit off <br />
- IT mixer tap lose <br />
- IT hot water dispenser tap repair<br />
- Fit new hot water tap senior <br />
- Fit off pool kitchenette <br />
- Fix centre in it dep Drain in remove IT hot water boiler clean off calcium build up inside re install<br />
- Supply and install new pilot injectors in commercial kitchen ovens due to the higher gas pressure for the new gas metre. <br />
- Draining a remove IT hot water tap again and inspect the internals, unit found to have faulty water level sensor have ordered new sensor. <br />
- Fit off dishwasher in pool kitchenette<br />
- Regas year 9 ac, 2kg 410a <br />
- check roof leaks arts <br />
- check new roof leaks cmw <br />
- check roof leak cmw foyer <br />
- check anchor points cm wood, middle school and southwood boys <br />
- check roof leaks caretakers <br />
- check AC caretakers <br />
- isolate gas caretakers <br />
- ij day roof leak, think it's spilled water<br />
- ELC blocked sink <br />
- ELC heaters 003, clean filters <br />
- gym office heater not working, coil iced up, need to check gas pressure, checked filter/ ordered a new filter <br />
- check roof anchor points arts building<br />
- Fix walkway downpipe to wall<br />
- Finnish of checking roof anchor points <br />
- regas gym AC 1kg R22<br />
- Canteen tap, tighten <br />
- ELC, check heater pressure as heaters are a bit hot <br />
- ELC supply and install replacement button tap in through <br />
- pool filter, modify bracket to suit new filters - ordered new bracket for new filters<br />
- Measure up and order new toilet suite arts <br />
- Inspect water leak in IJ Day switchboard, looks like water is coming from electrical conduit.<br />
-  Locate and measure all pits on site ready for confined space audit.<br />
- Supply and install new toilet in arts staff toilet <br />
- Finish inspecting pits <br />
- check roof leak in IJ Day switchboard with Alan<br />
<br />
Price include 2x Labourers <br />
- 1x 3 days <br />
- 1x 5 days<br />
<br />
Invoice sent 11/8/2019