Backflow Prevention Testing<br />
3x Backflow prevention devices annual testing. carried out the annual testing to three devices located at the main gates.<br />
Submit paperwork to Yarra Valley Water<br />
<br />
3x Backflow prevention devices annual testing. carried out the annual testing to three devices located at Science, Pool & Courtyard<br />
Supply test reports<br />
<br />
<br />
*** Backflow device at courtyard has failed for being too low to the ground, it needs to be raised to have 300mm clearance bellow it