Turn on and check all hot water units throughout school<br />
Clean inlet filter on Rinnai hot water for physics<br />
Thermostatic mixing valve testing, check all hot water outlets and record temperature throughout school<br />
Turn on gas to home ecc and commercial kitchen, relight all oven pilot lights<br />
Statcom mechanical services check<br />
Finance heater not working found cat had gotten under and destroyed the return air duct, supply and replaced return air duct and colourbond patch over hole<br />
Finance, chech roof penetrations for where possum was getting in, found bathroom cowling wasn't sealed, sealed all three cowels with wire mesh<br />
Junior reception roof leak above fan, found silicone on flashing had come away, cleaned off silicone and replace with new<br />
Principals AC check ac not heating, check gas pressure is a bit low will add gas <br />
Junior lib, check roof leak, lift side soaker flashing and can see water marks from water running over the rib, measured flashing.<br />
ELC burst water pipe, excavated and found fitting had burst, replaced with new and backfilled<br />
Remove leaking skylight and replace with roof sheet on boarding house<br />
Sewer jet and camera storm water drains at boarding house found that the injection leveling compound had blocked the drains<br />
Replace downpipes and rain head<br />
Middle school AC not working, attend site to inspect, found fault code so reset fault code and tested units<br />
