Attend site on Saturday with Non Destructive Digging (NDD) truck to excavate and locate burst fire main.<br />
Excavated and located a section old redundant 80mm copper fire main under the tree and found no leaks.<br />
Traced out neighbours water supply tappin and pothole excavated to prove watermain was 150mm blue PVC.<br />
Pothole excavated every metre along 150mm blue PVC water main to find leak, followed water main from driveway to where it disappeared under the road exposing 45* bend and found no leaks.<br />
Dial before you dig and Tintern Grammar fire plan show the fire main is a 150mm blue PVC main I was unable to find any leaks on the 150mm blue PVC main.<br />
I have isolated a valve in the street marked F/S and the leak has since stopped.<br />
<br />
Supply 2m3 of top soil and backfilled all excavations