Conducted CCTV survey of 150mm cast iron and earthenware sewer.<br />
<br />
Inspected from the pit in the gardenbed off walkway on the opposite side of the oval at the "Middle School".<br />
<br />
Surveyed 20M upstream from the pit. The drain is cast iron and in good condition. Inspected downstream through earthenware, 40M. Found a significant amount of root intrusion 15M downstream. Used high pressure water jet to clear roots. Jetted this section of drain to clear major roots at several joins.<br />
<br />
We have successfully cleaned the sewer in the section that has blocked most recently. Further investigation is required as to downstream access, condition of the drain beyond, and drain configuration in order to potentially provide a relining option.