- stem lab AC, check AC not working, replaced condenser fans, relocated thermostat to stem lab, test and commission, room heats to 19* with doors shut<br />
- check Library AC found Daikin not working, booked service call<br />
- science smell, check for gas leak, found floor waste traps had evaporated so poured water down them<br />
- colebrook hws terminator valve beeping, replaced batteries<br />
- busbay gutters, supply and install new gutters to busbay roof with down pipes terminating on adjacent roof<br />
- look at senior girls toilet running, supply and install new float inlet valve<br />
- Arts toilet blockage, remove toilet and camera drains found wipes blockage, clear blockage with cable machine<br />
- supply and install new gutters, rainheads and downpipes to lockerbay<br />
- fire hose hydrants and reels, service hydrant heads, replace washers, clean and reseat<br />
- supply and replace hose reels<br />
- flush all air from system and test reels<br />
- replace 2x roof sheets maintenance<br />
- statcom check extraction system<br />
- check oven thermostats, working fine<br />
- pond inlet valve, supply and install new valve<br />
- clean admin gate booster ready for painting<br />
- test and purge gas line after gas meter change over<br />
- supply and install new rainhead in courtyard