Tintern AC servicing 2022<br />
<br />
Performed complete service and maintenance on all AC's throughout<br />
Campus.<br />
<br />
Girls Junior School (P-2):<br />
- Serviced and tested all units. Cleaned fan barrels in 4<br />
indoor units. All units okay.<br />
<br />
Junior School (Reception):<br />
- Serviced all units including evaps and ducted unit.<br />
Cleaned 1 x fan barrel.<br />
<br />
Girls Junior School (3-6):<br />
- Found 2 x York split systems in C016 are not delivering<br />
cool air (low/no refrigerant).<br />
- Found C011 not functioning.<br />
- Evap serviced, tested and working.<br />
- All other units serviced, tested and all okay.<br />
<br />
Boys Junior School:<br />
- Serviced all units. Removed and cleaned fan barrels on<br />
the two admin offices (BS03 and BS02).<br />
<br />
C.M. Wood Performance Centre (First Floor):<br />
- All units serviced.<br />
<br />
C.M. Wood Performance Centre (Ground Floor):<br />
- Removed and cleaned fan barrels on units in WS32 and<br />
WS39.<br />
- All other units serviced, tested and all okay.<br />
<br />
Main Reception:<br />
- Found Yorks in rooms AS23, AS22, AS20, AS19, AS17,<br />
AS16 and AS15 are all delivering room temp air (low/no<br />
refrigerant).<br />
-All other units serviced, tested and all okay.<br />
<br />
Middle School:<br />
- All units serviced, tested and all okay.<br />
- VRV units thoroughly cleaned, see photos.<br />
<br />
Home Economics/Physics<br />
- 2 x evaps serviced, tested and all okay.<br />
- All other units serviced, tested and all okay.<br />
<br />
Girls’ Middle School (Year 9):<br />
- 2 units serviced, tested and all okay.<br />
Visual Arts:<br />
- Found units in rooms V001 (and adjoining room) not<br />
delivering cool air (low or no refrigerant)<br />
- Fujitsu Cassette in the middle area opposite v005 was not<br />
working. We found the condenser fan motor had become<br />
disconnected. We reconnected. Possibly faulty if still not working.<br />
- Removed fan barrels and deep cleaned the Daikins in the<br />
kitchen area<br />
- All other units serviced, tested and all okay.<br />
<br />
Science:<br />
- All units serviced, tested and all okay.<br />
<br />
Senior College:<br />
- All units serviced, tested and all okay.<br />
- Removed fan barrels and deep cleaned the units in rooms<br />
s007 and the room with the angled wall (Hitachi split) on<br />
the first floor. This room number is unmarked on the plans.<br />
<br />
Maintenance:<br />
- PS04 split system not operating.<br />
- All units serviced, tested and all okay<br />
<br />
Finance, Student Welfare, Community Services, Sports<br />
Center:<br />
- All units serviced, tested and all okay