Supply and install new DOL starter with thermal over load on fan.<br />
Reconnect extraction fans<br />
<br />
Remove, paint and re install cieling vent in office<br />
<br />
Fitoff lockerbay heater<br />
Check rook leak in IJ Day<br />
Run water and drain for new drinking fountain<br />
<br />
Jetter, jet clean and camera maintenance sewer line from pit to 60m along<br />
<br />
Check overflowing gutters colebrook office, found gutters dip in the middle and overflowed due to heavy rain<br />
Check overflowing rainhead in science courtyard<br />
Check roof leak colebrook toilets<br />
<br />
Check roof leaks CMW<br />
<br />
Clean up materials from term break work<br />
Clean blocked gutters from renderers<br />
<br />
Isolate all VRF ac systems for power peak load test<br />
Supply and replace urinal flush button in southwood boys toilets<br />
Measure and order new toilet seat fo ELC<br />
Measure and order CMW duct caps<br />
<br />
Jetter, jet and camera senior school stormwater<br />
Jet 150mm storm water under bus stop, removed buckets of exposed agg concrete wash off<br />
<br />
Fix leak at rear of quadrangle toilet block<br />
Supply and install new gutters, rain heads and downpipes to theatre<br />
<br />
Schedule in and shut down AC units ready for power peak load test<br />
Supply and fit new Daikin thermostat to Library glass room, set and program<br />
Attend school for water leak in colebrook lunch room, found Zip hot water was leaking<br />
<br />
Remove Zip hot water from Colebrook wing, open up unit to find leak, found burst connection, ordered new connection<br />
Check no water at garden tap at pavillion<br />
<br />
Check Southwood boys roof leak above smoke alarm, found it is the harness anchor point<br />
Check support ed heater not working found goats had unplugged it<br />
Pool air hander not working, reset and check operation<br />
Clean filters<br />
Supply and replace disabled toilet seat in elc<br />
Replace inlet valve on zip hot water boiler and reinstall<br />
Check ij day hot water boiler, adjust temperature<br />
Supply and replace filters to science ACs<br />
Remove screws on harness anchorpoint, fill hole with silicone and replace screws<br />
Schedule in board meeting to middle school AC system