Inspect roof leaks in senior college from underneath<br />
-remove ceiling tiles found silver paper had come away<br />
-found old ventilation penetration is leaking <br />
Inspect bubble in ELC car park<br />
Check roof leaks through visual arts bellow rainhead<br />
-cmw along window<br />
-southwood boys under ladder point<br />
-junior lib above desk<br />
-colbroke girls at evap vent<br />
Tap leaking at pavillion gates, found washer missing from sprinkler timer<br />
Inspect pits at pavillion with Al, found full of leaves<br />
Canteen combi oven<br />
-inspect water leaking from oven in canteen<br />
-3 o-rings have splits<br />
-water pump had leak<br />
-remove and service water pump grease up or rings<br />
-remove from elements have found one element had split<br />
-Supply and fit new element<br />
-supply and fit three new o rings<br />
-general service to Combi oven<br />
-refit oven re-commission all good<br />
Service and co test 10x  heaters in ELC<br />
-clean filters<br />
-carbon monoxide test All OK<br />
-gas pressure test<br />
-gas leak test All OK<br />
Walkthrough and check roof leaks from the storms on the weekend<br />
-check leaking toilet cistern in senior girls order new float valve<br />
Check colebrook girls toilets found water was turning black flashed all systems<br />
Replace tap washer in arts building<br />
Inspect roof leak in southwood boys B004, found original AC installer had put a penetration in the wrong space, removed his dektite and replaced with a new dektite re silicone and sealed.<br />
Inspect bubble in asphalt in ELC car park, trace water back up to the neighboring properties water meter, called Yarra valley water report the water issue<br />
Supply and install new flashing along base of pavilion<br />
Sika flex up all openings<br />
Supply and fit new heelguard grate to pit at rear of south of boys<br />
Supply new heelguard grate to pit when you channel drain has been installed<br />
Supply and install new fluidmaster inlet valve on senior girls toilet<br />
Linkfm<br />
-Check all extraction fans and system to home ECC and commercial kitchen<br />
-Sign off in online portal<br />
Fitoff dryer extraction fan in home ECC<br />
Bolt down grate southwood boys<br />
Service 8x heaters colebrook girls<br />
-clean filters<br />
-carbon monoxide test All OK<br />
-gas pressure test<br />
-gas leak test All OK<br />
Colbrook hall heatray heaters not working<br />
Inspect roof leaks, colbrook girl, replace loose screws, resilicone broken flashings, silicone split creases.<br />
IJ day inspect roof leaks found AC drains had split<br />
Supply and install condensation pump to it server AC that is leaking water<br />
Attend to roof leaks in junior library and hall way, found a few loose screws so removed and replaced with new, found a few gaps in window sills so silicone them up<br />
Attend to roof leaks in ij day, found drains to 2x ACs had perished so replaced with new drain pipe, found condensation pump not working so replaced with new.<br />
found silicone around dektites had warn away so cut away and replaced<br />
Senior college<br />
-remove old duct penetration from roof<br />
-patch with new roof sheets<br />
-remove all rubbish from roof<br />
-replace all ceiling tiles<br />
Home ECC roof leak<br />
-remove light to inspect leak found range hood flue was leaking<br />
-replaced all bolts in range hood fan and silicone up all bolts and holes on all three range hoods<br />
Finance<br />
-check all roof leaks, found a few pieces of flashing had come away, re siliconed holes.<br />
-removed old silicone from flashing with wire brush and replaced with new silicone.<br />
-found rotten timber, helped remove.<br />
-installed new flashing where rotten timber was removed from.<br />
-supply and replace 75mm downpipes with new 90mm downpipes and pops.<br />
-supply and install new dektite to AC unit pipe penetration<br />
Check roof leaks throughout the entire school after the weekend, found a few roof leaks are still present, have notified Graham.<br />
Check and inspect senior foyer roof leak found leaking around extraction fan flashing<br />
Inspection camera and map out stormwater drainage system from front exit gates back up through three pits back to the swimming pool.<br />
Reseat taps set senior male staff downstairs toilets found seat had a crack in it<br />
-order new basin <br />
Supply and install new basin set senior male staff downstairs toilet<br />
Install new sprinkler on oval<br />
Supply and fit new basin to senior girls upstairs toilets<br />
Supply and replace 2x float valves senior boys upstairs toilets<br />
Supply and replace 2x basin tap sets to gym boys change room<br />
Check roof leaks along windows of cmw staff room, found 2x leaks, will weather sheets when not raining<br />
Check roof leak junior library, removed wet tile<br />
Supply and install new rain head to downpipe at quadrangle