Visual Arts building please jet blast existing pipes and provide quote for new pipe works next holidays (June/July)<br />
Arts building -<br />
<br />
Conducted CCTV survey of 90mm stormwater outlet. Pushed up approximately 25M and<br />
found a small amount of roots. Jetted clear using high pressure water jet up to 25M.<br />
Relocated to downpipe next to cafeteria/canteen. Inspected and found root intrusions.<br />
Rodded 3 cables down with 3 inch cutter. Re-inspected approximately 16M downstream.<br />
Unable to survey further.<br />
<br />
*** A pit and sump pump is to be installed in the gardenbed as discussed